Inspect electrical board for standard operation
Email Aquatics coordinator with the details of rectification if action is taken
Manual bump is required. If you have been trained to do a manual bump, proceed and notify the Aquatics Coordinator
Have you completed a bump?
Ensure inlet/outlet valves (40 & 41) are fully open
Check contractors register for contractors currently on site completing works. If there is no sign of current works, re-open valves
Check Ecoline for leaks
- Standard operation
- Message: WATER TEMP HIGH
- Message: CHECK CELL/LOW SALT
- Message: PS TEMP HIGH
- Message: OVERLOAD CUT OFF
- Nothing displayed
Switch off at the wall, then switch it back on to do a hard reset. If the warning message still shows, the Aquatics Coordinator to contact Blake at AIS. Dose with Sodium Hypochlorite if FAC drops too low (isolate the Aquarius by closing valves 38 & 39)
Switch off at the wall, then switch it back on to do a hard reset. Between 0800-1600 weekdays contact FM Helpdesk and ask for an electrician to check the system. All other times, dose with Sodium Hypochlorite until issue is resolved.
Check Hydrochem service record (MONTHLY)
Ensure valves 38 & 39 are open
Ensure manual chemical dosing has not occurred in the last hour, then re-open the valves.
Check CO2 gas alarm for fault
Press reset. If the issue is not resolved, contact FM Helpdesk between 0800-1600 weekdays.
Visual inspection of chlorine circulation pump
- Normal operation
- Bump in progress
- One or more 'filter status' light is not glowing
Check again in 30 minutes, if the issue is not rectified then contact the Aquatics Coordinator
Ensure hot water lint pot does not have any leaks
Visual inspection of pool filtration pumps 1# & #2
Check balance tank sight glass level
Check pool filtration pump lint pots for leaks
Check heat circulation pumps for leaks, vibrations, and abnormal operating sounds
Any issues with the heat circulation pumps, contact FM Helpdesk between 0800-1600 weekdays, OR if the temperature drops 1 degree more than standard operation, contact FM Helpdesk outside these hours
Ensure fan is operating
Ensure lights are satisfactory
Ensure the CO2 tank is in working order (loading dock storage)
Current tank pressure
Turn off the blue isolation valve on the right hand side to build pressure then once in the green zone again, open blue isolation valve. You may need to dose acid in the meantime.