Bed Management / After Hours Coordinator
Oil level at start of test
Oil levels at completion of test
Fuel levels at start of test
Fuel Levels at completion of test
Emergency Capacity adequate for service delivery
Who was the inspecting company?
Has evidence of the last annual inspection been noted near the or inside the main generator compartment
Was the report free of deficiencies or service items needed
Prior communication sent to site
Pre test Approval provided by Bed Management
- MELBOURNE UNIVERSITY
- Local Power Authority
Personnel placed at high risk areas.
Lifts in secure position
Was the automatic transfer switch operated or exercised during the inspection [NFPA 110: 8.4.5]?
Total run time of the test
How long did it take for the generator to start
Local distribution boards reset
Comments regarding deficiencies or service items needed
Site returned to grid supply
Generator safe and visual inspection completed.