Previous years inspection reviewed
Test paperwork for systems on file in office?
Address Number on building complies to Chapter 70 of Gates Town Code, at least 4" and visible from roadway.
Occupancy sign posted for assembly buildings
For permitted occupancies is last years permit displayed?
Exits clear and unobstructed during drive around of property? Including snow and ice buildup.
Sidewalks, paths of travel maintained; no tripping hazards
Outside of the building in good shape? Ie no concrete spalling, missing siding, roof in good condition
- Type I
- Type II
- Type III
- Type IV
- Type V
- High Hazard
- Utility or Other
36" clearance in front of electrical panels
Extension cords not being used in place of permanent wiring
Combustibles not being stored in electrical equipment rooms
No open wiring, splices or junction boxes present
Air Flow sufficient to support proper operation
Chimneys and vent pipes intact and good condition
Heat producing device/appliance not defective.
Safety devices in place and operational
No storage of combustible with 18" of heat producing devices
Fire Alarm System
Inspected within the last year
No deficiencies noted on report
All devices present and appear to be in good condition on visual inspection
Fire alarm panel in normal or standby condition
Kitchen Suppression System
Inspected with the last 6 months?
No deficiencies noted in report
Kitchen hood clean and free from excess grease buildup?
Manual pull station unobstructed and visible
Class "K" extinguisher present?
Fire Sprinkler System
Inspected within the last quarter?
No deficiencies noted on the report
Sprinkler valves and riser accessible?
Visual inspection of components, not dust loaded, intact an in good condition
Proper number and type of spare heads in cabinet along with sprinkler wrench?
FDC is unobstructed, couplings work easily and show no sign of damage
Outside horn/strobe or bell appears to be in good condition and not obstructed in any way
Extinguisher tagged with an inspection tag, sealed and has the proper pressure
Extinguishers accessible and not blocked or impeded in any way?
Extinguishers mounted on the wall or in extinguisher cabinets
Extinguishers proper type and size for hazards present
Exit signs illuminated during inspection
Emergency lighting operational during inspection?
Documentation of the annual 90 minute test available?
All exterior exit doors close and latch on their own.
Fire doors closed or held open by magnets controlled by the fire alarm system.
Fire door tags in place on doors and door assemblies?
No combustible storage in exit ways
Exit ways unobstructed?
Aisle width compliant?
All exits open easily and are unobstructed.
Door hardware compliant?
Fire lanes properly marked and unobstructed?
Fire department access roads maintained and unobstructed?
Annual test paperwork available or on file in fire marshal office
3' clearance maintained around hydrant
Compressed gas tanks stored properly and secured to prevent them from accidentally tipping over. NYS Fire Code Chapter 30
Stored in approved containers or cabinets
LP gas stored outside in approved cages and provided with vehicle impact protection. NYS Fire Code Chapter 38
MSDS paperwork available?
Tier II reporting being done?
If it is not have them contact Dave Richards at 585-753-3813 or firstname.lastname@example.org
Interior combustible waste not excessive Section 315
Location of dumpsters in proximity to the building. Dumpsters must be kept a minimum of 5' from any combustible wall, openings or overlapping roof eaves
No openings in walls or ceilings
Penetrations in fire walls caulked and sealed?
No combustible storage in mechanical, boiler or elevator rooms
Maintain storage at least 2' below the ceiling.
No combustible storage under stairways