Panel is unobstructed?
Has a risk assessment been carried out to determine adequate detector coverage?
Are detectors of the correct type for the risk?
Are the detectors correctly situated within each protected area?
Is the panel protect by a clearly identified circuit breaker?
Is the panel numbered or identified?
A suitable and up to date zone chart is in place?
The panel was found to be powered up and operational?
The date of installation of the standby batteries is clearly shown on the units?
The panel is securely fastened?
The panel is locked?
Internal wiring is secure with all exposed conductors insulated?
Battery disconnected and fault signal received?
Fault signal activates internal buzzer?
Power disconnected and fault signal received?
Manual call point activated and fire signal received?
Main siren activated upon receipt of fire signal?
Decibel range tested correct?
Flashing light on siren unit activates?
Smoke applied to at least 10% of detectors?
Fire signal received at each test?
MCP 's tested?
Fire signal received at each MCP test?
Has the staff received adequate training in the acceptance of alarms, faults and other related procedures?
System passed all tests and is certified as compliant?